Buy ASTM D SPECIFICATION FOR GLASS-FIBER-REINFORCED POLYESTER UNDERGROUND PETROLEUM STORAGE TANKS from SAI. ASTM D Standard Specification for Glass-Fiber-Reinforced Polyester Underground Petroleum Storage Tanks CONTAINED IN VOL: – Find the most up-to-date version of ASTM D at Engineering
|Published (Last):||26 March 2007|
|PDF File Size:||10.22 Mb|
|ePub File Size:||10.43 Mb|
|Price:||Free* [*Free Regsitration Required]|
SECTION 22 50 00 FUEL OIL PIPING SYSTEM PART 1 – GENERAL
Handle fuel oil system components carefully to avoid damage to material component, enclosure and atsm. Aging management guideline for commercial nuclear power plants – tanks and poolsreportFebruary 1, ; Albuquerque, New Mexico. End fitting of connectors shall conform to pipe fitting types specified elsewhere.
Valve shall be iron body, Buna-N diaphragms, and brass piston and cylinder.
MIL-T A TANKS STORAGE UNDERGROUND GLASS FIBER
Provide an electronic monitoring system to monitor the fuel oil level in the fuel oil storage tank, monitor the tank for leakage and detect the presence and amount of water in the tank with the fuel.
Search Inside This report can be searched. The following text was automatically extracted from the image on this page using optical character recognition software:.
Provide astj complete fuel oil supply system including pumps, piping, fittings, valves, controls and accessories as specified and required for a complete and operating system. Install piping, valves and fittings to make fuel systems complete. Install fiberglass piping systems in accordance with the manufacturer’s written installation constructions. Should any item wstm system fail to perform in acceptable manner, adjust, remodel, or replace dd4021 or items as required.
All reference amendments adopted prior to the effective date of this Contract shall be applicable to this Project. This specification covers glass-fiber-reinforced horizontal, cylindrical, and spherical-type underground tanks for atmospheric pressure storage of petroleum based fuels and oils. Probes shall be temperature compensated asgm correct for fuel oil temperature variations.
Pumps shall be interlocked to automatically shutdown when a low level is sensed in the main storage tank via a d421 contact closure in the fuel level monitoring system. Avoid sudden or excessive pressure surge which could produce failure or whipping action due to sudden release of stored energy. Following is a list of organizations and the titles of a few of their standards or codes that relate to UST management:. Provide positive electrical pump and motor grounding in accordance with requirements of the NEC.
Provide Neenah or approved equal H 20 rated [gasketed,] steel traffic cover manholes, minimum 24″ diameter. Documents Flashcards Grammar checker. Show all pages in this report. State environmental compliance is probably your biggest job challenge—the regulations and laws are so complex and they change so fast! Location of leaks shall be detected by covering all connections with mild soap solution and watching for leaks during pressure tests.
Aztm monitoring system shall be capable of detecting leakage rates as small as 0. Cut sheets of pipe and fittings, valves, pumps, pump controllers, monitoring equipment wstm other required accessories clearly indicating all features, options, materials and dimensions.
Pumps shall be [submersible] single stage type, bronze fitted, bronze impeller, and stainless steel shaft. Store fuel oil system components in a clean, dry space and protect from the weather.
Pipe shall be clean and free of sand and grease at connection ends. At the Contractor’s option, all underground piping may be installed in a single secondary containment.
Valves shall astj designed to reduce psi to 20 psi in the fuel oil return line and shall be rated for psi WOG. Valves shall be furnished with blowoutproof stems. The control panel shall be designed for two individual incoming power circuits. The installer has been certified by the tank and piping manufacturers.